Page 1:Features & Specifications
Page 2:Unboxing Video
Page 3:Teardown & Component Analysis
Page 4:Load Regulation, Hold-Up Time & Inrush Current
Page 5:Efficiency, Temperature & Noise
Page 6:Protection Features & DC Power Sequencing
Page 7:Cross-Load Tests & Infrared Images
Page 8:Transient Response Tests
Page 9:Ripple Measurements
Page 10:EMC Pre-Compliance Testing
Page 11:Performance, Value, Noise & Efficiency
Page 12:Final Analysis
Transient Response Tests
Advanced Transient Response Tests
For details on our transient response testing, please click here.
Ιn these tests, we monitor the HCG1000 Extreme's response in several scenarios. First, a transient load (10A at +12V, 5A at 5V, 5A at 3.3V, and 0.5A at 5VSB) is applied for 200ms as the PSU works at 20 percent load. In the second scenario, it's hit by the same transient load while operating at 50 percent load.
In the next sets of tests, we increase the transient load on the major rails with a new configuration: 15A at +12V, 6A at 5V, 6A at 3.3V, and 0.5A at 5VSB. We also increase the load-changing repetition rate from 5 Hz (200ms) to 50 Hz (20ms). Again, this runs with the PSU operating at 20 and 50 percent load.
The last tests are even tougher. Although we keep the same loads, the load-changing repetition rate rises to 1 kHz (1ms).
In all of the tests, we use an oscilloscope to measure the voltage drops caused by the transient load. The voltages should remain within the ATX specification's regulation limits.
These tests are crucial because they simulate the transient loads a PSU is likely to handle (such as booting a RAID array or an instant 100 percent load of CPU/GPUs). We call these "Advanced Transient Response Tests," and they are designed to be very tough to master, especially for a PSU with a capacity of less than 500W.
Advanced Transient Response at 20 Percent – 200ms
Advanced Transient Response at 20 Percent – 20ms
Advanced Transient Response at 20 Percent – 1ms
Advanced Transient Response at 50 Percent – 200ms
Advanced Transient Response at 50 Percent – 20ms
Advanced Transient Response at 50 Percent – 1ms
Voltage drops on the +12V and 5V rails were controlled well.
On the 5V rail, deviations were larger than we like to see. Meanwhile, the 3.3V rail was this PSU's worst performer. In most test scenarios, the 3.3V rail's voltage dropped below 3.2V.
Here are the oscilloscope screenshots we took during Advanced Transient Response Testing:
Transient Response At 20 Percent Load – 200ms
Transient Response At 20 Percent Load – 20ms
Transient Response At 20 Percent Load – 1ms
Transient Response At 50 Percent Load – 200ms
Transient Response At 50 Percent Load – 20ms
Transient Response At 50 Percent Load – 1ms
Turn-On Transient Tests
In the next set of tests, we measure the HCG1000 Extreme’s response in simpler transient load scenarios—during its power-on phase.
For our first measurement, we turn the power supply off, dial in the maximum current the 5VSB rail can handle, and switch the PSU back on. In the second test, we dial the maximum load the +12V rail can handle and start the PSU while it is in standby mode. In the last test, while the PSU is switched off, we dial in the +12V rail's maximum load before restoring power. The ATX specification states that recorded spikes on all rails should not exceed 10 percent of their nominal values (+10 percent for 12V is 13.2V, and 5.5 V for 5V).
There were no significant spikes or voltage overshoots to report. Still, the curves we recorded weren't the smoothest we've seen.
- Features & Specifications
- Unboxing Video
- Teardown & Component Analysis
- Load Regulation, Hold-Up Time & Inrush Current
- Efficiency, Temperature & Noise
- Protection Features & DC Power Sequencing
- Cross-Load Tests & Infrared Images
- Transient Response Tests
- Ripple Measurements
- EMC Pre-Compliance Testing
- Performance, Value, Noise & Efficiency
- Final Analysis